HOW DO I?
Monterey County Declares Hepatitis A Outbreak Among Homeless Population
Since early 2017, the San Diego and Santa Cruz County Health Departments have been investigating local hepatitis A outbreaks among individuals who are homeless or use illicit drugs. Unfortunately, disease levels in Monterey County have now reached outbreak levels. Since October 2017, hepatitis A has been diagnosed in 9 individuals with a history of homeless in Monterey County. These individuals did not travel outside of Monterey County so are assumed to have become ill due to transmission within the homeless and illegal drug use communities in Monterey County.
2/5/2018 4:46:00 PM
Monterey County Animal Control Program Advisory Board Meeting
Monterey County Animal Control Program Advisory Board will meet Thursday, March 22nd at 3:30 pm at the Monterey County Animal Services Center, 160 Hitchcock Road in Salinas
3/19/2018 11:49:00 AM
Bayer Issues Recall of Alka-Seltzer Plus® Products
Bayer is voluntarily recalling Alka-Seltzer Plus® packages that, were sold only in the U.S. at Walmart, CVS, Walgreens and Kroger (including Dillons Food Stores, Fred Meyer, Fry’s Food Stores, Ralphs, King Soopers and Smith’s Food and Drug) after February 9, 2018. The packages can be identified by checking the Bayer logo located on the lower left corner of the front of the carton. If the logo has an orange or green background, the product is included in the recall The affected packages are being recalled because the ingredients on the front sticker may not match the actual product in the carton.
2016 California’s Chapter 15 of the California Plumbing Code (CPC) (as of 2017, previously it was in Chapter 16) titled, “Alternate Water Sources for Nonpotable Applications”, which covers regulations on reuse of reclaimed (recycled) water, gray water, and on-site treated nonpotable gray water.
Chapter 15 of the California Plumbing Code: Clothes Washer System
A clothes washer system does not require a construction permit as specified in Section 220.127.116.11 and may be installed or altered, but must follow the below requirements:
- If required, notification has been provided to the Enforcing Agency regarding the proposed location and installation of a graywater irrigation or disposal system.
- The design shall allow the user to direct the flow to the irrigation or disposal field or the building sewer. The direction control of the graywater shall be clearly labeled and readily accessible to the user.
- The installation, change, alteration or repair of the system does not include a potable water connection or a pump and does not affect other building, plumbing, electrical or mechanical components including structural features, egress, fire-life safety, sanitation, potable water supply piping or accessibility. Note: The pump in a clothes washer shall not be considered part of the graywater system.
- The graywater shall be contained on the site where it is generated.
- Graywater shall be directed to and contained within an irrigation or disposal field.
- Ponding or runoff is prohibited and shall be considered a nuisance.
- Graywater may be released above the ground surface provided at least two (2) inches (51 mm) of mulch, rock, or soil, or a solid shield covers the release point. Other methods which provide equivalent separation are also acceptable.
- Graywater systems shall be designed to minimize contact with humans and domestic pets.
- Water used to wash diapers or similarly soiled or infectious garments shall not be used and shall be diverted to the building sewer.
- Graywater shall not contain hazardous chemicals derived from activities such as cleaning car parts washing greasy or oily rags, or disposing of waste solutions from home photo labs or similar hobbyist or home occupational activities.
- Exemption from construction permit requirements of this code shall not be deemed to grant authorization for any graywater system to be installed in a manner that violates other provisions of this code or any other laws or ordinances of the Enforcing Agency.
- An operation and maintenance manual shall be provided. Directions shall indicate the manual is to remain with the building throughout the life of the system and indicate that upon change of ownership or occupancy, the new owner or tenant shall be notified the structure contains a graywater system.
- Gray water discharge from a clothes washer system through a standpipe shall be properly trapped in accordance with Section 1005.0
When running a bleach or dirty diaper laundry load the system would need to be switched to the sanitary sewer or septic system (except bleach or other harsh chemicals which can impact the bacteria health of your system).